according to EN12101 part 9 and 10 with own fire detectors
Control unit RZ8
Building-authority approved hold open unit control with operation and display foil and the possibility to connect up to 2x20 fire detection elements. It is applicable for external activation through a superior control unit. The transfer of the activation signal to other control units is effected by an isolated contact. Control and supply of up to 3 smoke barriers an their detector.
Signal connection with other control units via potential relay contact (end position open and closed).
Central fire alarm system
Additional activation via central fire alarm system is possible.
max. safeguarding 10A
Connection and monitoring of the optical smoke detectors is effected by a hold open unit.
Driving motor with locking device
The 230V alternating current motor used for electrical opening and works according to the fail-safe-principle. An AM-I is integrated in the drive unit and enables automatic speed control for the closing process and the 24VDC supply of the hold open unit.
Every smoke barrier can additionally be activated through a manual activator (push button).
This tender as a PDF! You can find the general PDF tender document for this control unit here.
We would like to help you personally! You will find our contact information here. And certainly you can always use our contact form .